J – 8 to 24 Zone Expandable Control panel. FireClass J Details Manuals / Documents Approvals / Declarations of Conformity. MAIN FEATURES. BENTEL SECURITYsrl shall not assume the responsibility for damage arising from improper application or use. Manual Extinguishment Input. + Add to cart. Specification; Documents. Manufacturer. BENTEL. Part number. J Number of zones. 8. Zone expansion up to. Supply voltage. V AC.
|Published (Last):||2 December 2004|
|PDF File Size:||15.84 Mb|
|ePub File Size:||11.13 Mb|
|Price:||Free* [*Free Regsitration Required]|
Expander Modules Accessing the Programming session Enrolling: The J and J Control panels provides the follo – wing features: Silence status will be signalled by: This module provides written infor – long pause lasting 5 seconds ; Z24 and the Test key simultaneously. Telecom Mains Mains Disab.
Bentel Security | Products > Fire Products > Repeater Panel – JREP
Manual Automatic valve Ext. Display Door screws Unless otherwise stated, the numbers in boldface in this Keyswitch Access Level 2.
Flat cable accessory item: Installing the Extinguishment Module observed. Install the Extinguishment Module, as follows.
Remove the screws 4 and open the Control panel. Expander Module Install Expander Modules as follows. Expanders Modules must be installed befo- re mounting the Control panel to the wall. Remove the screws 4 bfntel open the Con- trol panel. Insert the reverse locking supports 93 into their respective locations 94 as per Fig.
Installing Repeaters Installing the Control panel Work carefully through the following steps see the Fi – The Display Module if used must be installed be- gures on pages 10, 12 and Operating principles This Normally-Open Output open-collector will: Up to 1 A can circulate on the PR Output. Module for fire extinguishment purposes up to benrel Extin- Ack. These devices have been specially designed To activate an Alarm when the Control panel is in Module will generate the Pre-extinguishment phase which will be signalled by: The device concerned bemtel been restored Table 2 Event Descriptions Continues PS Input of Extinguishment Mod.
Fire panel sticker J – EN
PS Input of Extinguish. The Silence button can be used during Access Le – vel 2 only. ON glowing indicates that the program – med Investigation time is running. Figure 15 Wiring diagram of 3 detectors with Normally-Open Outputs and a Call point with zero ohm contact resistan – ce: The power cable must be routed as per Figure 21c and held The following operations must carried out regularly.
Output Voltage of the Switching Power Supply to the indicated value. Extinguishment Modules You can program this system from the Control mamual or from a computer, using the J application.
The Extinguishment Modules page will allow you to This section describes how to program the system from enrol and set up Extinguishment Modules, as follows. Disable Extinguishment Input [IE] terminals. The delay countdown will follows. To download a specific page: Once the operating parameters have been set up, they To Download several pages: Time option Key 0respectively, to increase or decre Press Enter or Esc to confirm and go back to the Main menu.
Page of 64 Go. Table of Contents Add to my manuals Add.
Bentel J424 Installation Manual
Related Manuals for Bentel J No related manuals. Introduction 3k5 of IEC Page 10 Logic Extinguish.
Page 12 Figure 2 Maximum configuration of janual J Control panel Display Door screws Unless otherwise stated, the numbers in boldface in this Keyswitch Access Level 2 Page 15 Flat cable accessory item: Installing Repeaters Installing Repeaters Installing the Control panel Work carefully through the following steps see the Fi – The Display Module if used must be installed be- gures on pages 10, 12 and Page benhel Module for fire extinguishment purposes up to 2 Extin- Ack.
Button n Pre-extinguishment Phase n Manual Extinguishment If the programmed extinguishment conditions occur The Extinguishment Module can be activated from ma – programmed by your Installerthe Extinguishment nual call-points ask your Installer for details.
Connecting Call-points Figure 15 Wiring diagram of 3 detectors with Normally-Open Outputs and a Call point with zero ohm contact resistan – ce: Connecting A Power Supply 60 and jumper connectors. This manual also for: Comments to this Manuals Your Name. Enter text from picture: By pressing ‘print’ button you will print only current page. To print the manual completely, please, download it.
Don’t show me this message again. Got it, continue to print. Don’t have an account?